Complete Water Solutions was called out for an emergency to get our client’s Reverse Osmosis System back up and running. The problem that they were experiencing was High Conductivity, High Pressures & Low Flow.
Upon arrival it was determined that the RO System had experienced hard water. Complete Water Solutions tested the water to confirm the hard water. Upon further inspection Complete water was able to determine that the bypass valve on the softeners had been opened. Once closed the hard water went away. In the mean time complete water solutions supplied and installed new AK4040F Membranes into the RO System. This lowered the conductivity, pressures and increased flow.
Need Membranes Or Service Contact Complete Water Solutions email@example.com